Nutone QT9093WH Quiet Bathroom Fan with a Heater and Room Light
Quiet QuieTTest ventilation in classic Heater, Fan and Light combination fixture. Quick heat with efficiently designed 1500w heating element and aluminum blower to distribute heat evenly.
Polypropylene blower exhausts odor, steam and stale air. Includes quiet non-metallic back draft damper.
Automatic reset thermal protection.
Expansion-type hanger bars for joists up to 24" o.c.; mounting brackets adjust for up to 3⁄4" plaster thickness.
Detachable junction box features three (3) wiring knockouts.
One-piece die cast grille with pebble-texture bezel is available in White Enamel. 8" diameter glass lens extends only 3" from ceiling.
Wall switch with separate on/off controls for all four functions is included with each unit. Or, may be used with any standard in-line thermostat to control the heat cycle.
1500w heating element and aluminum blower to distribute heat evenly.
100 watt incandescent bulb (NOT INCLUDED)
(1) 7w bulb (for night light). Purchase bulbs locally.
HVI Certified bathroom fan.
1 Year Warranty
15 3⁄8" diameter
3" extension from ceiling.
8 1/8 W
13 Ό L
7 ½ D
110 CFM (air flow)
1500 total watts
120 Volts hard wired
20 Amp Circuit Only
12 gauge wire
4 round duct connection (4 Exhaust Duct NOT INCLUDED)
4 Way wall switch with separate on/off controls for all 4 functions
Front Cover / Grille
Observe all requirements in this instruction sheet and all markings appearing on the unit.
Check all operations of the unit after installation has been completed.
The heater housing must be grounded and the wiring must comply with all local electrical codes.
The flange of the rough-in housing MUST be flush with the finished plaster or drywall surface to assure proper and absolutely safe operation.
If plaster material, paint base or paint is sprayed on the walls or ceiling, the inside of the housing must be masked off to prevent this material from entering the housing.
The switch (furnished) must be wired in accordance with the wiring diagram.
For installation in sloped ceilings up to 12/12 pitch.
Ductwork must point up.